Label: Under what circumstances will thermal runaway occur during UPS battery
float charging? Under normal circumstances, the UPS battery float voltage is 2.23V/cell (25°C), and the maximum charging current is not more than 25%A of the rated capacity. When the temperature is below 0C or above 40C, it is necessary to correct the charging voltage. With 20C as the starting point, for every degree change, the single cell voltage changes -3mv. If the total voltage during the charging process or the indicator value of the voltmeter on the indicator plate deviates from the reference value (±0.05V/single cell) during floating charging, the cause should be investigated and dealt with. If you do not work in this floating charge range, but use 2.35V/cell (25℃), thermal runaway will occur after 4 months of continuous charging; or use 2.30V/cell (25℃) and charge continuously for 6~ Thermal runaway will occur in 8 months; if 2.28V/cell (25°C) is used, severe capacity drops will occur for 12 to 18 consecutive months, leading to thermal runaway.
An increasing dependence on the use of sealed lead acid battery top lead acid battery manufacturers has made numerous changes in the top lead acid battery manufacturers industry over the past decades.
Shenzhen Power Kingdom Co., Ltd. ’s mission is to provide high quality care and services to our members and to be profitable in the process.
The development of top lead acid battery manufacturers sealed lead acid battery products has massive potential for expansion.
You can get more information from Power Kingdom for on sale. welcome to visit us and send your inquiry!