Many people think that the battery does not need maintenance, especially when using UPS power supply, this idea is more obvious. But in fact, the problems caused by the lack of maintenance of batteries account for a high proportion of all UPS failures. Therefore, routine maintenance of the UPS battery
will greatly extend the UPS battery life and reduce the failure rate. This article will introduce how to maintain UPS batteries. maintain an appropriate ambient temperature Generally speaking, the larger factor that affects the battery life is the ambient temperature. Generally, the best ambient temperature required by battery manufacturers is between 20-25°C. Although the increase in temperature improves the discharge capacity of the battery, the price paid is that the life of the battery is greatly shortened. According to the test, once the ambient temperature exceeds 25°C, the battery life will be shortened by half for every 10°C increase. At present, the batteries used in UPS are generally maintenance-free sealed lead-acid batteries
, and the design life is generally 5 years, which can only be achieved under the environment required by the battery manufacturer. If the specified environmental requirements are not met, the length of their lifespan will vary greatly. In addition, the increase of the ambient temperature will lead to the enhancement of the chemical activity inside the battery, thereby generating a large amount of heat energy, which in turn will promote the increase of the ambient temperature. This vicious circle will accelerate the shortening of the battery's life. Regularly charge and discharge the float voltage and discharge voltage in the UPS power supply have been adjusted to the rated value at the factory, and the size of the discharge current increases with the increase of the load. The load should be adjusted reasonably during use, such as controlling the microcomputer The number of electronic equipment used. Under normal circumstances, the load should not exceed 60% of the UPS rated load. Within this range, the battery discharge current will not be over-discharged. Because UPS is connected to the mains for a long time, in an environment with high power supply quality and few mains blackouts, the battery will be in a floating state for a long time, which will cause the battery's chemical energy and electric energy to convert between the activity and accelerate the aging. And shorten the service life. Therefore, it should be completely discharged every 2-3 months, and the discharge time can be determined according to the capacity of the battery and the size of the load. After a full-load discharge is completed, charge it for more than 8 hours according to regulations. Using the communication function At present, most large and medium-sized UPSs have operability such as communication with microcomputers and program control. Install the corresponding software on the microcomputer, connect the UPS through the serial/parallel port, and run the program, then the microcomputer can be used to communicate with the UPS. Generally, it has functions such as information query, parameter setting, timing setting, automatic shutdown and alarm. Through information query, you can obtain information such as mains input voltage, UPS output voltage, load utilization, battery capacity utilization, internal temperature and mains frequency; through parameter settings, you can set the basic characteristics of UPS, battery life and The battery runs out of warning, etc. Through these intelligent operations, it greatly facilitates the use and management of the UPS power supply and its storage battery. timely replacement of used/bad batteries The number of batteries currently equipped with large and medium-sized UPS power supplies ranges from 3 to 80, or even more. These single batteries are connected by circuits to form a battery pack to meet the needs of the UPS for DC power supply. In the continuous operation and use of UPS, due to the difference in performance and quality, it is inevitable that individual batteries will be damaged due to performance degradation and insufficient power storage capacity. When one/some batteries in the battery pack are damaged, the maintenance personnel should inspect and test each battery to eliminate the damaged battery. When replacing a new battery, you should try to buy the same type of battery from the same manufacturer, and it is forbidden to mix acid-proof batteries, sealed batteries, and batteries of different specifications. This article gives four ways to extend the working life of UPS batteries. In general, they can be summarized in four sentences: proper temperature, regular charging and discharging, good use of communication functions, and timely replacement of damaged batteries. There are no university or elementary school questions in the study of power supply. As long as you pay attention to observation, you can summarize various characteristics and methods to facilitate our design.
Shenzhen Power Kingdom Co., Ltd. is considered as one of the leading supplier of sealed lead acid battery products in China.
There is always a question of how to top lead acid battery manufacturers, but have you ever thought about the price point? Go to Power Kingdom to get cost effective offer.
can be used in a wide variety of ways.
In business, sealed lead acid battery means cultivating brand loyalty; once someone is working with a product or using a service, they are more likely to commit to paying for Power Kingdom again.
is something that has been around for a few decades now, enjoying it's heyday back in the top lead acid battery manufacturers.